If any error occurs in your air conditioner, indoor display shows error codes. Once you nail down the issue you can easily call in a professional, or fix the issue yourself. To help you out we have listed down the most common error codes of Lennox AC.
Indoor Unit Error Display
|E0||EEPROM parameter error|
|E1||Indoor/outdoor units communication protection|
|E2||Zero-crossing signal error|
|E3||Indoor fan speed out of control|
|E5||Open or short circuit of outdoor temperature sensor or outdoor unit EEPROM parameter error|
|E6||Open or short circuit of room or evaporator temperature sensor|
|E7||Outdoor fan speed out of control|
|P0||IBM malfunction or IGBT over-strong current protection|
|P1||Over voltage or too low voltage protection|
|P2||Temperature protection of compressor top|
|P4||Inverter compressor drive error|
Lennox Split AC
If there is an error occurring during the operation of the system, the error code will be displayed on the LCD, as show in Fig.5.1. If multi errors occur at the same time, their codes will be displayed circularly.
|E1||High pressure protection.|
|E3||Low pressure protection.|
|E4||High discharge temperature protection.|
|E5||Whole unit over-current protection.|
|E6||Indoor and outdoor communication error.|
|E7||Running mode conflict.|
|E9||Indoor unit full water error.|
|EU||Frequency restricted/reduced with IPM temperature protection.|
|EL0C||Refrigerant leakage detection.|
|EH61||Evaporator coil middle temperature sensor T2 is in open circuit or has short circuited.|
|F0||System charge shortage or blockage protection.|
|F1||Return air temperature sensor open/ short circuited.|
|F2||Evaporator temperature sensor open/ short circuited.|
|F3||Outdoor ambient temperature sensor open/ short circuited.|
|F4||Outdoor unit condenser mid-tube temperature sensor open/short circuited.|
|F5||Discharge temperature sensor open/ short circuited.|
|F6||Frequency restricted/reduced with overload protection.|
|F8||Frequency restricted/reduced with whole unit current protection.|
|F9||Frequency restricted/reduced with high discharge temperature.|
|FH||Frequency restricted/reduced with antifreezing protection.|
|H3||Compressor overheating protection.|
|H5||IPM Current protection.|
|HE||Compressor demagnetization protection.|
|P5||Over phase current protection.|
|P6||Drive board communication error.|
|P7||IPM temperature sensor open/short circuited.|
|P8||IPM Temperature Protection.|
|P9||AC contactor protection.|
|PD||Sensor connection protection.|
|PE||Temperature drift protection.|
|PF||Drive board temperature sensor error.|
|PH||DC bus over-voltage protection.|
|PL||DC bus under-voltage protection.|
|PP||AC input voltage abnormal.|
|PU||Capacitor charging error.|
|PC00||Inverter module IPM error.|
|PC01||High or Low voltage protection.|
|PC02||High temperature sensed at compressor top.|
|PC03||Low or High pressure protection.|
|PC04||Inverter compressor drive error.|
|PC08||Current overload protection.|
|PC0L||Outdoor low ambient temperature protection.|
|U1||Compressor phase current sensing circuit error.|
|U3||DC bus voltage drop error.|
|U5||Whole unit current sensing circuit error.|
|U7||4-way valve reversing error.|
|U8||PG motor zero-crossing protection.|
|L3||Outdoor fan 1 error protection.|
|LA||Outdoor fan 2 error protection.|
|LC||Compressor startup failure.|
|LD||Compressor phase loss/reversal protection.|
|LP||Indoor and outdoor units unmatched.|
|B5||Indoor unit liquid valve temperature sensor open/short circuited.|
|B7||Indoor gas valve temperature sensor open/ short circuited.|
|DN||Communication line misconnected or expansion valve error.|
|105||Device communication failure|
|124||Active subnet controller missing|
|126||Internal control communication failure|
|131||Corrupted control parameters|
|132||Failed flash CRC check|
|180||Ambient sensor problem|
|400||Compressor internal overload trip|
|401||Long run time. Compressor is running extremely long run cycles|
|402||System pressure trip.|
|403||Short cycling. Compressor is running less than three minutes|
|404||Locked rotor. Compressor has a locked out due to run capacitor short, bearings are seized, excessive liquid refrigerant|
|406||Open start circuit|
|407||Open run circuit|
|408||Welded contactor. Compressor always runs|
|409||Secondary low voltage.|
|410||Low pressure fault|
|411||Low pressure switch lockout|
|412||High pressure fault|
|413||High pressure switch lockout|
|414||Discharge line temperature fault|
|415||Discharge line temperature lockout|
|417||Discharge sensor fault|
|Ds11, Ds13, Ds14, Ds15||OEM mode. Factory test mode|
Note: In event of any error, please turn off the unit and contact the professionally skilled personnel.
Lennox Air Conditioner Mini Split
Indoor and Outdoor Error Codes
Climatic 50 Roof-Top, Aircoolair & Compactair Version 24
|004||Filters, Clogged up|
|006||Recovery Module, Filters, Clogged up|
|011||Electric heating elements|
|012||High Temperature, Blowing|
|013||Low Temperature, Ambient|
|022||Low Temperature, Blowing|
|023||High Temperature, Ambient|
|051||Recovery Module, Motor failure|
|052||Recovery Module, Wheel failure|
|081||Temperature sensor, Ambient|
|082||Humidity sensor, Ambient|
|083||Temperature probe, Outside|
|084||Humidity sensor, Outside|
|085||Temperature probe, Blower|
|086||Circuit 1, Temperature sensor, Water condenser Outlet|
|087||Circuit 2, Temperature sensor, Water condenser Outlet|
|088||Temperature sensor, return or Mixing air|
|096||Low temperature, Water Condenser|
|097||High temperature, Water Condenser|
Lennox AC Troubleshooting
Please check below items before asking for maintenance.
Phenomenon: Indoor unit can’t receive remote controller’s signal or remote controller has no action.
- Whether remote controller is within the signal receiving range?
- Whether there are obstacles?
- Whether remote controller is pointing at the receiving window?
- Is sensitivity of remote controller low; fuzzy display and no display?
- No display when operating remote controller?
- Fluorescent lamp in room?
- Signal receiving range is 8m.
- Remove obstacles.
- Select proper angle and point the remote controller at the receiving window on indoor unit.
- Check the batteries. If the power of batteries is too low, please replace them.
- Check whether remote controller appears to be damaged. If yes, replace it.
- Take the remote controller close to indoor unit.
Phenomenon: No air emitted from indoor unit
- Air inlet or air outlet of indoor unit is blocked?
- Under heating mode, indoor temperature is reached to set temperature?
- Heating mode is turned on just now?
- Eliminate obstacles.
- After reaching to set temperature, indoor unit will stop blowing out air.
- In order to prevent blowing out cold air, indoor unit will be started after delaying for several minutes, which is a normal phenomenon.
Phenomenon: Air conditioner can’t operate
- Power failure?
- Is plug loose?
- Air switch trips off or fuse is burnt out?
- Wiring has malfunction?
- Unit has restarted immediately after stopping operation?
- Whether the function setting for remote controller is correct?
- Wait until power recovery.
- Reinsert the plug.
- Ask professional to replace air switch or fuse.
- Ask professional to replace it.
- Wait for 3min, and then turn on the unit again.
- Reset the function.
Phenomenon: Mist is emitted from indoor unit’s air outlet
Check items: Indoor temperature and humidity is high?
Solution: Because indoor air is cooled\rapidly. After a while, indoor temperature and humidity will be decrease and mist will disappear.
Phenomenon: Cooling ( heating) effect is not good
- Voltage is too low?
- Filter is dirty?
- Set temperature is in proper range?
- Door and window are open?
- Wait until the voltage resumes normal.
- Clean the filter.
- Adjust temperature to proper range.
- Close door and window.
Phenomenon: Outdoor unit has vapor
Check items: Heating mode is turned on?
Solution: During defrosting under heating mode, it may generate vapor, which is a normal phenomenon.
Phenomenon: ”Water flowing” noise
Check items: Air conditioner is turned on or turned offjust now?
Solution: The noise is the sound of \refrigerant flowing inside the unit, which is a normal phenomenon.
Phenomenon: Cracking noise
Check items: Air conditioner is turned on or turned offjust now?
Solution: This is the sound of frictioh caused by expansion and/or contraction of panel or other parts clue to the change of temperature.
Lennox Air Conditioner Manual PDF
- Rheem Pool Heat Pump Error Codes With Solutions - May 31, 2023
- Danby Portable AC Error Codes – Problems and Meaning - May 25, 2023
- Teco AC Error Codes and Troubleshooting – How to Fix It - May 25, 2023
13 thoughts on “Lennox AC Error Codes – (2023 Latest Fixes and Updates)”
I have an error code at the compressor E410. pls help
Hello Nclave, first of all, thank you for visiting our website.
If your air conditioner is still under warranty, the best option would be to call in a service team. The service team will diagnose the issue and take the necessary steps for repair.
However, if the warranty has expired or you’re looking for a quicker solution, there are a few steps you can try yourself.
E410 Low pressure fault.
1. Restricted air flow over indoor or outdoor coil.
2. Improper refrigerant charge in system.
3. Improper metering device installed or incorrect operation of metering device.
4. Incorrect or improper sensor location or connection to system.
If these steps do not work, I would recommend reaching out to the technical service of the device. I hope this issue gets resolved quickly and your air conditioner works smoothly again. If you have any questions or need further assistance, please let me know.